Consequences of Omitting Sprinklers from concealed spaces
From a prevously recorded webinar: This lesson will discuss the advantages and disadvantages and of omitting sprinklers in concealed spaces. It can be maddening trying to determine what the minimum remote area size permitted. We will discuss how section 188.8.131.52 ties in with the calculation section of 184.108.40.206.4. We will help you answer the question, “Will I need to use a minimum remote area of 3,000 square feet?”
Upon completion of this lesson, participants will be able to:
Clearly identify the section of NFPA 13 that applies to any concealed space.
Determine if sprinklers are required in any concealed space
Determine if the calculation area must be 3,000 square feet or larger in size
Utilize NFPA 13 calculation method to achieve the most cost effective fire sprinkler system where concealed spaces are present.
Duration: 60 Minutes
Presenter: Cecil Bilbo
To enroll in this class or find out more information, login to your account at the top of this page.