After replacing the battery module follow the steps below.
- Place the CHECKFIRE 210 System into isolate mode using the isolate switch on the side of the ICM.
- Press and hold the programming button for more than five seconds then release.
- All programming LEDs pulse 3 times in one second to confirm battery life indicator is reset.
- Cancel isolate mode by returning the isolate switch to the normal position.
When connected to the ANSUL CHECKFIRE 210 Programmer software, click the Reset button in the Battery Life Remaining section.
CHECKFIRE 210 Detection and Actuation System